Piping HFC-227EA fire protection system is a clean agent fire suppression system, it very suitable for suppress fire in large space, From an economic point of view, if a protection zone have many rooms, then a piping HFC-227ea system will be the best for that.
HFC-227ea is a technical name, and its full name is “heptafluoropropane”, this is a colourless, odourless halo-carbon, the founder Dupont named another commercial name for it called ” FM200″, so when we say FM200 system, it is HFC-227ea clean agent fire protection system.
HFC-227ea clean agent fire protection system is gas total flooding system for large space fire protection, such as: computer room, data center, switch-gear, server room etc.
It usually work with completely fire alarm systems, when a fire occurs in the protected area, the heat detectors and smoke detectors will find out there is a fire, then send out a fire signal to the fire control panel, the fire control panel then will give instructions to the fire alarm and gas releasing indicator, makes alarm bell alarming and gas releasing indicator flashing, after 30 seconds time delay the HFC-227ea fire suppression system will start to total flooding the fire automatically.
This is pipying FM200 system, if some projects require to install non-pipying system, please refer to our 2.5 MPA CABINET TYPE FM200 SYSTEM.
The piping system has its features in the following points:
It normally be applied and installed in some larger space:
Just to be on the safe side, equipment maintenance and repair must be established and completely according to the international and China regulations.
During the maintenance and repair process, relevant regulations specified under GB50263-2007 " the Specifications of Gas Extinguishing Construction and Acceptance must be strictly performed.
If during the maintenance and repair job, you are suffer from problems, please search for help from our company, the user must notify our company via correspondence or telephone and emails.
This product must be maintained by professional technical personnel or our authorized distributors.
For International Standard, refer to NFPA 2001-Standard on Clean Agent Fire Extinguishing Systems. buy and download the relative documents if necessary.